Distribution Garage Units
18th Edition Garage units:
Garage, PV and EV sub distribution units conform to BS EN 61439-3 using Doepke 40 Amp RCCB with maximum 100A BS 88 fuse link: Icc < 10kA
For installations with Icc < 16kA refer to the Consumer Unit selection Tab at the top of this page.
Note : Any electrical equipment installed in garages, utility rooms, sheds or buildings directly attached to or in close proximity to a domestic (household) premises must be contained in a metal enclosure.
|Garage Unit - Type A RCCB|
Refer to Technical Data for additional information
Incoming Outgoing MCBs RCCB 1 2 Reference
40A 30mA 16A 6A DGU1.MP2X
Product Standard: BSEN61439-3
- High quality 4 module IP2X metal enclosure
- 0A 30mA Type A RCCB supplied as standard
- For other cofigurations including Type F or B RCCBs please contact us
On request, we can assemble custom units for applications requiring the use of different types of RCCB e.g. F, AKV, AEV, FEV, BSK or BNK.
Supplied in Metal (IP2X) or Insulated enclosures* (IP55):
For price and availability, please email your specification to firstname.lastname@example.org.
*Note: Insulated enclosures where appropriate, may be used in installations not covered by Regulation 421.1.201
Custom unit including A-KV RCCB